Auto Recloser Circuit Breaker Working Principle
1.Applications of MCB/RCCB with auto reclosing
MCB/RCCB with auto reclosing can be widely used in power grid terminal lines, such as meter box, solar energy circuit management, PV solar control box, smart electricity, smart home system, new energy vehicle charging pile, and so on.
2.Working principle of auto recloser
The working rule of an auto-recloser is equally simple: when a fault is detected, the breaker trips. The controller then waits for a predetermined time before reclosing the breaker. If all is well, that’s the finish of the process, but if the fault persists the breaker trips again and, after an extra delay, the controller recloses it for a second time and checks again for the continuing presence of the fault. If the fault remains present after this second recloses, the breaker trips once more.
3.Functions of automatic circuit recloser
- It can be matched with a circuit breaker/leakage protection switch and automatically reclose when MCB / RCCB trips unexpectedly, no need for manual closing, reduce the cost of manual maintenance, and eliminate faults in time to improve efficiency.
- Built-in many reclosing times, continuous closing failure within a few minutes can send an alarm through auxiliary contact.
- With manual / automatic selector switch.
- With mechanical/electronic double locking function.
- The shaft transmission mode is more stable and reliable.
- Can match other accessories.
- Work status is indicated by LED.
4.Auto recloser circuit wiring diagram（Take GEYA GRD9L-R as an example）
5.Installation of auto recloser circuit breaker（Take GEYA GRD9L-R as an example）
1.If auto recloser cooperates with RCCB:
First, put the linkage device into the RCCB’s handle.
Then close the upper and lower buckles to ensure that they are tightly connected.
2. If auto recloser cooperate with MCB：
First, put the linkage device into the handle of the MCB,
Then align the small cylinder to the corresponding hole
Finally, close the upper and lower buckles to ensure they are tightly connected
3.If auto recloser cooperate with MCB/RCCB and accessories：
First, install the MCB/RCCB on the rail
Then, install the automatic reclosing device (ARD)
Finally, install the accessories next to the ARD
6.Operation of automatic recloser
AUTO mode, the auto reclosing function is enabled：
MANU mode, the auto reclosing function is disabled. MCB/RCCB can only be opened and closed manually：
When powered on, the green indicator will flash for 2 seconds to wait for the power supply to stabilize. Then the green indicator light will stay on if when MCB / RCCB fails to trip, the red indicator light will be on. Note that red during auto reclosing delay, the color will flash. After the delay, it will switch on automatically and the green light will be on:
If you are interested in ordering automatic reclosing in bulk, please contact us directly! We offer preferential prices for bulk orders!